Gutters and the Indoor Pool
Gee, wonder why this house smells DAMP?
Cellar vents were BELOW Grade? (see the red line, that was the level of the ground)
Step 1: Brick up all the vents
Step 2: Grade the ground so water flows away from the foundation. This took an entire dump truck full of backfill.
This project might sound boring, but just read on a moment. The first day when we viewed the house with the real estate agent, the house smelled damp. No it wasn’t because it had been shut up and empty. It WAS damp. Humidity in the crawlspace was 98%.
Luckily it rained the next day so we could see what the problem was. When I saw what they had done, I stood there speechless…. I could NOT fathom why anyone would do this.
They emptied the gutters into the crawlspace!
Gutters on one half of the house meet alongside the front door. Where to drain them? Can get past the steps. Why not punch a hole in the foundation and dump the water in the crawlspace? Maybe they wanted to build An Indoor Pool?
Yes, that’s what they did. Do I need to repeat that?
Hundreds of gallons of water were evaporating into the crawlspace under the house. No wonder no one wanted to buy the place. Luckily, the fix was simple and cost less than $200.
Whenever you do work or have someone do it, look for any critical errors in the design.
OK, I can see that they wanted to carry the drain through the house. Fine. But there were TWO critical flaws:
- They used LANDSCAPE pipe. This is the corrugated stuff that lightly connects. It is NOT supposed to be water tight. With every rainfall, it leaked at least 100 gallons. It spread that water ALL over the crawlspace.
- They dumped the landscape pipes into into the house’s emergency french drain. Then, every time it rained, the long trench inside the cellar filled up with rainwater. It eventually drained out, but it left a large area soaked like a SPONGE. All this then evaporated into the crawlspace area driving the humidity to 100%. Yes, they had a brand new $2000 dehumidifier. But guess what? It had failed and nobody checked.
The fix cost maybe $200 in parts…
And a lot of labor. I had to run about 90 feet of 6″ SOLID PVC. This picked up the gutters drains at one end, flowed through the house and exited through the wall. I ran the pipes parallel to the existing serer drains. Looks good and keeps the plumbing together.
And YES, I installed several Access Ports so you can inspect or clean the lines.
To get the water OUT of the house I cut a hole in the block below grade (and sealed it from both sides) and then ran the pipe underground in a 3′ deep trench until the ground fell away and let the water run off. Shame I could not have captured that water and used it for irrigation!
Within DAYS of finishing this project the cellar started to dry out. The company that sold the dehumidifier agreed to repair it under warranty and now the conditioned space is livable space.